- Completed inspection on tablet.
- Recovered freon from system. Removed and replaced high and low side schrader valves. Vacuumed system. Charged freon to proper capacity. Inspected AC lines and drive belt. Verified proper operation of AC system. compressor leaking and expansion valve wet with dye.
- replaced leaking compressor and o-rings.
- replaced leaking expansion valve and o-rings.
Don C. gave our service a 5 star review on 4/8/2021